tmpx wall post indicator
6 TFP1 Page of Installation Vertical Indicator Post Step 1 Step Step 3 Step 1. Rotate Gate Valve Top ap clockwise to fully open Gate Valve. Step. Remove Wrench from Post ssembly. Loosen Set Screws. Remove Screw, Washer, and Eyebolt. Step 3. Remove ap ssembly from Post ssembly. Step Step Step Step. Remove Extension Rod from Post ssembly. Step. Temporarily mount Post ssembly to Gate Valve Indicator Flange and secure with four bolts and nuts (not included). Step. Loosen Screws and Lock Nuts securing Upper Pipe to Lower Pipe. djust Upper Pipe, aligning Mark Ring height with finished grade. Step 7 Step Step 9 11″ (0 mm) Step 7. Tighten Screws and Lock Nuts to secure Upper Pipe to Lower Pipe. Step. Loosen onnect ap Set Screws. Temporarily Install Extension Rod ssembly in Post ssembly, engaging Gate Valve Top ap by onnect ap. Step 9. Mark Extension Rod 11 inches (0 mm) above top of Upper Pipe. Remove Extension Rod ssembly. Evenly cut Extension Rod at marked location.
1 Worldwide ontacts Resilient-Seated Gate Valves with Vertical or ross Wall Post Indicator General Description TYO Resilient-Seated Gate Valves with Vertical and ross Wall Indicators are used in fire protection systems for on/off operation. End connection configurations including Flange by Flange, Flange by Groove, and Groove by Groove are available. The ductile iron body weighs approximately 0% less than conventional cast iron valves, which allows easier handling on site and reduced shipping costs. The fully encapsulated EPDM ductile iron wedge ensures drop-tight sealing. Valve components are either inherently corrosion-resistant or protected with fusion-bonded epoxy resin coating for a long, reliable service life and enhanced UV protection in exposed installations. This valve is one of the lightest, most durable gate valves on the market today. Its design features and material selection criteria fulfill the need for a reliable, long life and easy to operate gate valve. These valves are available with either Vertical Indicators for underground water supplies or ross Wall Indicators for interior water systems. oth indicators provide external visual indication of the open or shut valve condition as well as a locking mechanism to secure a particular wedge position. NOTIE Never remove any piping component nor correct or modify any piping deficiencies without first de-pressurizing and draining the system. Failure to do so may result in serious personal injury, property damage, and/or impaired device performance. It is the designer s responsibility to select products suitable for the intended service and to ensure that pressure ratings and performance data are not exceeded. Material and gasket selection should be verified for compatibility with the specific application. lways read and understand the installation instructions. TYO Gate Valves described herein must be installed and maintained in compliance with this document, in addition to the standards of any other authorities having jurisdiction. Failure to do so may result in serious personal injury or impair the performance of these devices. The owner is responsible for maintaining their mechanical system and devices in proper operating condition. The installing contractor or device manufacturer should be contacted with any questions. Technical Data Sizes (DN0), (DN10), (DN00), (DN0), and (DN300) pprovals FM pproved UL Listed Maximum Working Pressure FM – 3 psi (1 bar) UL psi (0,7 bar) Flanges SME 1.1/SME 1. EN 9-/ISO 700-/ Drilled to NSI /10, PN/PN1, or S 9 (Table E) Materials of onstruction See individual valve and indicator parts lists, Figures 1,, and. Page 1 of DEEMER 013 TFP1
Page 1 of 12 DECEMBER 2013 TFP1545
Maximum Working PressureFM – 232 psi (16 bar)UL – 300 psi (20,7 bar)
As one ‘use case’ for aligning symbols is to enable them to be placed ‘near’ to another symbol, and be always positioned appropriately at a variety of output scales, I am going to suggest that U: components for user friendly point symbols should always be just a little greater than half the symbol dimension. ie the light blue box should enclose the symbol. That way, an aligned symbol can always leave a pleasing small gap from its insertion point.
distributed under the GNU General Public License.